This standard specifies requirements for design, planning, installation, operation and maintenance for fire alarm systems in conjunction with DIN VDE Alarm systems for fire, instrusion and hold-up; Requirements for fire detection and alarm systems. Alarm systems for fire, intrusion and hold up; Part 2: Requirements for fire alarm systems.
|Published (Last):||24 July 2013|
|PDF File Size:||12.79 Mb|
|ePub File Size:||5.17 Mb|
|Price:||Free* [*Free Regsitration Required]|
This is stated 1: Depending on the status of implementation in building legislation in 08332 federal states, the “two senses principle” should apply to alerting systems. Making the right choice The planning and configuring of audible and visual fire alarm systems must fulfill many conditions. The product standard also requires the devices to deliver a specific light output and light distribution.
The right choice of alerting solutions must be made for each application in accordance with VDE Furthermore, increasing numbers of people worldwide suffer from hearing defects and for them a purely audible alerting system is not effective. There can be good reasons to use a clear light, particularly in industrial vvde. On the other hand, Category “O” open installation allows the manufacturer to describe the coverage volume in any way or to design the best possible coverage volume for specific applications and constructions.
May Number of pages: It will no longer be permitted to use visual and visual-audible signaling devices which were licensed for use in fire alarm systems before that unless they were already on the market. For example, it specifies that throughout the coverage area a minimum light intensity of 0.
Fire protection in accordance with VDE – Pfannenberg
The following article explains the significance of this development for suppliers, installers and designers of fire alarm systems. It is crucial that an alarm concept is drawn up in advance in order to define the hazardous areas. The preferred color for alarms is red. Fire detection and fire alarm systems – Part Gestion des risques Author s: April 08333-2 of pages: Several challenges vvde a project in a school were solved in this way.
AFNOR Editions Online Store
Industrial buildings normally have high ceilings and large surface areas which clearly define the coverage volume. The ZVEI fact sheet 1 summarizes the principles and challenges of visual alarm systems: Louisot Date of publication: In these cases, the use of signaling devices in the “O” category are recommended as they can be positioned with some flexibility enabling the coverage volume to be as wide as possible.
Fire protection in accordance with VDE Fire alarm systems are stipulated in building legislation and their use is regulated under the special provisions for construction.
Downtime due to upgrades and modernizations in the relevant areas were reduced to a minimum. NF X June Safety instructions and information – Orders and instructions, evacuation plans, intervention plans, safety plans and safety technical documentation.
Fire alarm systems in both cases fulfill their purpose of allowing fire to be detected at dih early stage, irrespective of whether people are present or not, so that appropriate action can be taken without delay.
Rescue service personnel can therefore intervene quickly and extinguish a fire before it has taken hold. Knowing the actual coverage volume of the signaling devices provides as much certainty as possible throughout the whole project phase and guarantees that the alarm system will be compliant with the standards, thus achieving the objectives and preventing costs from rising excessively.
The most important change resulting from the new VDE for FSA suppliers, installers and planners is that every alerting solution must be planned individually. As before, DIN VDE stipulates unequivocally that the operator of a system is responsible for the fire alert and alarm concept. Register online rin inter and intra-company training, and certifying diplomas, seminars, distance learning. Integration in the FDNet intelligent bus system from Siemens is particularly easy because parameterization can be carried out with the software that puts the system into operation.
DIN VDE – October
One of the benefits of loop signaling devices is simple installation in public buildings. Installation rules for fire detection systems. For visual alarm systems, the individual coverage volumes in the relevant approval category must now be arranged so that they cover the whole of the space throughout which the signal is to be seen. Depending on the product and the application, the choice of signaling color a clear or a red cover can have an effect on the coverage volume and therefore on the number of signaling devices required.
Alarm systems for fire, intrusion and hold up – Part 2: The components are largely harmonized in the EN 54 series of European standards.
Beaulier Date of publication: Purchase More information add to basket. February Number of pages: